Missing existing soil type info., missing seismic design parameters, incompl. RISA Floor/3D computer input/output, missing HVAC anchorage details,/calcs, incomple. AFSS submittal (1/19/12). Addn docs recvd 2/2, 2/7 & 2/9/2012.
all local fire requirements must be included in the scope of this application. INCLUDE IN BACK REVIEW: all site plan corrections per local fire instructions + AOR must address all of CBC chap 7A requirements + civil drawing related changes per local FD requirements[FLS]. RETURNED FLS CIVIL AND AFSS RESUBMITTAL PLAN REVIEW ON 7.6.12.
HPI fee was received on 5/18/2012 and processed on 5/21/2012.**The HPI score under CEC 2008 and CHPS 2009 is 32.RPG**